|Item||Single Wall Flexible Vent Pipe|
|End Type||Snaplock Coupling|
|For Use With||Ameri Flex Single Wall Appliance|
- Sized to fit outlet. Use sheet metal screws for code approved appliance connection.
- Single Wall Connector Systems
- The Ameri-Flex single wall connector system is UL Listed as a vent connector for installation as specified in the National Fuel Gas Code (ANSI Z 223.1, NFPA 54), NFPA 211, and other model codes such as Uniform Mechanical Code, National Mechanical Code, and Southern Mechanical Code. Single wall flexible vent connector connects one or more appliances to double wall Type B Gas Vent. Use for listed gas appliances with a draft hood or other gas appliances listed for use with Type B Gas Vent. Flexible Pipe: 0.012" aluminum alloy 3003. Single wall pipe ends: 0.018" aluminum-zinc coated steel. Rigid components: 0.018" aluminum-zinc coated steel. Clearance: 1" to combustibles. Do not enclose. Do not pass through walls, floors, or ceilings.