|Type||Conduit/Unit Mount (Hydronic Application)|
|Transformer Primary (V)||120|
|Transformer Secondary (V)||24|
|Resistive Amps @ 120V||10|
|Full Load Amps @ 120V||7.4|
|Locked Rotor Amps @ 120V||44.4|
|Resistive Amps @ 240V||6|
|Full Load Amps @ 240VAC||3.7|
|Locked Rotor Amps @ 240V||22.2|
|Application||Hydronic Heating Systems|
|Includes||Auxiliary Contacts For Switching Additional Low or Millivoltage Loads, Millivolt Rating 300 Ma Minimum At 750 mV. Low Voltage Rating, Pitot Duty 50 VA At 24VDC, Rating 1Amp At 12 VDC.|
- Magnetic and Transformer Combination Relays
- Install in any position. Snap-acting for remote control of air conditioning, heating, and ventilation systems, and to control fans, blowers, motors (up to 1-1/2 HP), tools, and other electrical devices within ratings.
- Transformer Combination
- 120V primary, except 2E346 is 240V and 2E857 has enclosed relay. 2E346 features conduit hub or screw mounting.
Average Product Rating: 3based on 1 reviews
LoudWednesday, November 02, 2011
I replaced two older Honywell units that had wires that were starting to corrode. They worked silently and obviously had better built transformers in them. These replacements warn about humming and to isolate them from a wall mount which I did but they still have an aggravating hum when energized. They cheapened them up too much.