|Item||Hazardous Location Receptacle with Disconnect Switch|
|Number of Wires||2|
|Number of Poles||3|
|Mounting Box||Copperfree Aluminum|
|Finish||Epoxy Powder Coat|
|NEMA Rating||3, 3R, 4, 4X, 9FG|
|Standards||UL 1010 (UL1203), UL 894, UL 1682, UL 1686, UL Listed for Class II, Division 1 and 2, Groups F, G; and Class III|
- Disconnect switch allows safe connect and disconnect operation at 20, 60, or 100A, 600VAC max. The circuit breaker allows connect and disconnect operation in addition to short circuit and thermal time delay overload protection. DBR Series are Class II, Div. 1 and 2, Groups F and G. Class III and are NEMA rated 3, 3R, and 9FG. EBR Series meet Class I, Div. 1 and 2, Groups C and D Class II, Div. 1 and 2, Groups F and G and are NEMA rated 3, 3R, 4, 4X, 7CD and 9FG.