Hazardous Location Receptacle with 480VAC EHD Breaker, Voltage 600VAC Max., Hz 60, Amps 100, Number of Wires 3, Number of Poles 4, Hub Size 1-1/2 In., 3/4 In., Mounting Box Copperfree Aluminum, Material Copperfree Aluminum, Finish Epoxy Powder Coat, Standards UL 1010 (UL1203), UL 894, UL 1682, UL 1686, UL Listed for Class I, Division 1 and 2, Groups C, D, Class II, Division 1 and 2, Groups F, G; and Class III
Hazardous Location Receptacles
- Disconnect switch allows safe connect and disconnect operation at 20, 60, or 100A, 600VAC max. The circuit breaker allows connect and disconnect operation in addition to short circuit and thermal time delay overload protection. DBR Series are Class II, Div. 1 and 2, Groups F and G. Class III and are NEMA rated 3, 3R, and 9FG. EBR Series meet Class I, Div. 1 and 2, Groups C and D Class II, Div. 1 and 2, Groups F and G and are NEMA rated 3, 3R, 4, 4X, 7CD and 9FG.