Split System Heat Pump21, 500 BtuH Cooling, 25, 000 Reverse Cycle Heat BtuH, Voltage 208/230, SEER 16.5, 60 Hz, 1 Phase, Min. Circuit Amps 15, Max. Time Delay Fuse Amps 20, HSPF 9Operation Mode Auto/Cool/Heat/Dry/Fan, Additionally The Zones Can Be Run Independently, Indoor Units DrillSpot # 2TLP6, 295 And 2TLP7, 355 CFM High, Indoor Units DrillSpot # 2TLP6, 260 And 2TLP7, 305 CFM Medium, Indoor Units DrillSpot # 2TLP6, 220 And 2TLP7, 250 CFM Low
Friedrich Ductless Split System Air Conditioners
- Units reach and maintain set point quickly for energy efficiency. Operate in 0 to 115 F ambient temp. Oscillating up/down louvers and continuous air sweep. Mount low against wall or on ceiling. Multizone units provide heating and cooling off 1 outdoor condenser and up to 4 separate indoor units (zones); independent LCD remote control for each zone. Automatically switch between cool and heat. New installations require refrigerant line set, sold separately.
- AHRI Certified performance. ETL and C-ETL Certified.
- Single and multizone models 24-hr. programmable timer and sleep timer Auto restart after power outage Dehumidification and auto-fan modes Environmentally friendly R-410A Installation requires qualified technician