Split System Heat Pump35, 200 BtuH Cooling, 38, 000 Reverse Cycle Heat BtuH, Voltage 208/230, SEER 15.0, 60 Hz, 1 Phase, Min. Circuit Amps 22.5, Max. Time Delay Fuse Amps 30, HSPF 9Operation Mode Auto/Cool/Heat/Dry/Fan, Additionally The Zones Can Be Run Independently, 2 Indoor Units DrillSpot # 2TLP6, 295 And 1 Indoor Unit 2tlp8, 415 CFM High, 2 Indoor Units DrillSpot # 2TLP6, 260 And 1 Indoor Unit 2TLP8, 355 CFM Medium, 2 Indoor Units DrillSpot # 2TLP6, 220 And 1 Indoor Unit 2TLP8, 290 CFM Low
Friedrich Ductless Split System Air Conditioners
- Units reach and maintain set point quickly for energy efficiency. Operate in 0 to 115 F ambient temp. Oscillating up/down louvers and continuous air sweep. Mount low against wall or on ceiling. Multizone units provide heating and cooling off 1 outdoor condenser and up to 4 separate indoor units (zones); independent LCD remote control for each zone. Automatically switch between cool and heat. New installations require refrigerant line set, sold separately.
- AHRI Certified performance. ETL and C-ETL Certified.
- Single and multizone models 24-hr. programmable timer and sleep timer Auto restart after power outage Dehumidification and auto-fan modes Environmentally friendly R-410A Installation requires qualified technician