|Type||3 Piece Oil Lubricated Booster|
|Face to Face Dimension||6 3/8 inches|
|Max. Temp. (F)||225|
|Max. Working Pressure (PSI)||125|
|GPM of Water @ 1 Ft. of Head||32|
|GPM of Water @ 2 Ft. of Head||30|
|GPM of Water @ 3 Ft. of Head||28|
|GPM of Water @ 4 Ft. of Head||25|
|GPM of Water @ 5 Ft. of Head||23|
|GPM of Water @ 6 Ft. of Head||19|
|GPM of Water @ 7 Ft. of Head||15|
|GPM of Water @ 8 Ft. of Head||9|
|Length||14 7/8 inches|
|Width||4 1/4 inches|
|Feet of Head @ 5 GPM||8|
|Feet of Head @ 6 GPM||8|
|Feet of Head @ 7 GPM||8|
|Feet of Head @ 8 GPM||8|
|Feet of Head @ 9 GPM||8|
|Feet of Head @ 10 GPM||7|
|Feet of Head @ 12 GPM||7|
|Feet of Head @ 15 GPM||7|
|Feet of Head @ 18 GPM||6|
|Feet of Head @ 20 GPM||5|
|Feet of Head @ 25 GPM||4|
|Feet of Head @ 30 GPM||2|
|Max. GPM @ Head (Ft.)||32 @ 1|
|Best Efficiency GPM @ Head (Ft.)||17 @ 6|
|Min. GPM @ Head (Ft.)||9 @ 8|
|Includes||Gaskets, Bolts, and Oil|
|SKUs||4RD16, 70101, 70101|
The closed-loop Bell & Gossett Series 100 Inline Circulator Pump is designed for use in domestic and light commercial water circulating systems, such as hydronic heating and low-pressure boosting. The motor on this pump is oil-lubricated which, along with the three-piece design, provides for easy field service. The shaft and seal are housed in an assembly that can be easily repaired or replaced. This pump's motor design, coupled with its overall hydraulic performance, allows the Bell & Gossett Series 100 to overcome system-related noise caused by valves, fittings, or piping. And resilient mounting provides quiet, dependable service with minimum annual lubrication.
The Bell & Gossett 106189 features a precision ground pump shaft is oversized to provide large bearing surfaces and a hardened integral thrust collar minimizes end-thrust to ensure long seal and bearing life. The mechanical seal is designed to withstand the wide range of water temperatures, pressures, additives and dissolved solids common in hydronic systems.
The Bell & Gossett Series 100 comes with gaskets, bolts, and oil. Not for use in potable water systems. This pump may also be referred to by the Bell & Gossett model number 100NFI. UL, CSA listed.Due to legislation, this product is restricted from use in drinking water applications. To expedite the handling of your order, please include a confirmation in your order notes stating that this product will not be used for drinking water. Any order that is for drinking water applications may be cancelled.
Average Product Rating: 4.7based on 18 reviews
HappyThursday, March 14, 2013
Even last-minute plans can come togetherWednesday, March 13, 2013
The previous unit (same model) lasted at least 15 years, new unit has better design for the housing, so it will probably outlast me.
Refurb units at discount might be attractive.
the best!!!!!Tuesday, March 05, 2013
Exactly what I needed and it went together perfect.THANK YOU drillspot!!
Everything,the price,as well as the small things..bolts,seals,oil,everything.
Bell & Gossett 106189 1/12 HP Series 100 Circulator Pump SKU: 70101Tuesday, January 22, 2013
Excellant Purchase, Fast Shipping, All Parts in package needed to install. Fit perfect! Thanks for the fast delivery and excellant product. Jim Johnson
Every thing needed in box to install and oil pump.
Great pumpFriday, January 04, 2013
I really can't say anything bad about this product. I have a very old hot water boiler system heating my home. My old Series 100 developed a leak. I'm sure it was about 40-50 years old. This new pump is a direct replacement. Installation was easy. I know there are alternative pumps that cost much less but after seeing how long my original one lasted, I had no problem replacing it with the same type.
The price could be better but again, after seeing how long it lasted, I'm sure the higher price will wash out when other pumps fail earlier.
just what i neededSaturday, December 08, 2012
exactly what i needed. directions were clear. beat the store price by 25%.
Hot Water Heat Circulator PumpTuesday, November 06, 2012
Pump wase a perfect fit. Easy replacement. Works great.
Gaskets & new bolts included.
It is made in China, rather if it would be made in US
PumpingTuesday, October 23, 2012
I was shocked when I visited my local dealer and found out this model was selling for $545.00. After just a short google search I found the same model and warrantee on DrillSpot.com for half the price! The site was easy to navigate, checkout was quick and delivery was on time. Thanks Drillspot for making a bad situation better!
Ease of install
Match the original electric connection which is located on the bottom of motor not top
Great PumpTuesday, January 31, 2012
This pump works great and is so quiet you can barely hear it run, the one it replaced was very old and noisy that rattled my pipes. UPDATE: pump made it 24 days before becoming so noisy it woke me at 2:30 am out of a sound sleep, took apart and found pump is very stiff barely turns. Was oiled when installed as per instructions, unit is now made in china like everything else and is apparently junk.
Circulator PumpTuesday, January 17, 2012
Received on time. Pump is just like the orignal. Fit perfect, and is running good. Put the new one in a week ago that i had sitting for 6 years then a week later the other one went out, and the one I ordered from Drillspot did not get to sit very long. I have a 2 pump system. Hopefully I should be good for a few years. By all means, the price was right. A big savings compared to local dealers. You can feel safe dealing with Drillspot.
Just what I wanted
100 Series PumpTuesday, January 03, 2012
Just what I needed. Thank you very much.
It fixed me right up
Perfect ReplacementWednesday, December 21, 2011
I was very satisfied with this product along with all the necessary bolts, gaskets, and directions to replace this unit. Fast delivery and in ten minutes time I had the system running again.
Great Service!Tuesday, December 13, 2011
Thanks so much for the Bell and Gossett 1/12 HP Series 100 Circulator Pump. It is an excellent piece of equipment, well-made and sturdy and I'm hopeful that it will help keep my house warm for many years to come! It was delivered promptly and worked perfectly.
Furnace RepairTuesday, October 18, 2011
Good product, exact replacement. I hope it will last another 50 years.
Apartment OwnerTuesday, August 23, 2011
I have been very satisfied with 100 circulator pump. The one I am replacing is the same pump. It has been running continuously for many years. It is my fault that it stopped running. I failed to oil it on time.
Apartment BuildingTuesday, July 26, 2011
Purchase this to replace a Bell and Gossett pump that never worked in my apartment building when I purchased it 8 years ago. Replacement was easy and everthing aligned exactly. So far the the pump works great!
Easy to install
AmazedFriday, May 06, 2011
I was pleasently supprised when I saw this was so recently manufactured. At such a cheap price, I was expecting old stock or something.
It's a great pump at a great price.
The oil containment could be improved. Of course, I probably over oil it.
Good ServiceThursday, March 03, 2011
This works real nice compared to the smaller pump I had before. I can feel the difference in heating the second floor. Good product and good service from Drillspot.com.